Class 5, ecodesign boilers
Boilers for export
Be our installer
We invite you to cooperate with C.O. boiler installers. Please complete all required fields, otherwise your application will not be accepted.
Be our distributor
We invite you to cooperate with wholesalers and stores. Please complete all required fields, otherwise your application will not be accepted.
KWM-SG heating furnaces were designed to be used in central heating installations in flat buildings, trade pavilion, workshops, on farms, in glass-houses, schools, etc. Heating furnaces were granted ecological attestations and conformity certificates according to standard PN-EN 303-5 issued by the Institute of Chemical Processing of Coal in Zabrze and certificates issued by Technical Supervision Office for WE – module B1 project investigation.
Body of the KWM-SG heating furnace consists of furnace chamber and heat exchanger both made of high quality attested steel. Furnace has cuboidal shape, on its walls there are air nozzles and on the bottom there is water grate made of attested thick-walled pipes.
In KWM-SG heating furnace there are convection ducts located in the upper part of the heating furnace (upper duct) formed as “shelves”, where one of them is made in a form of griddle with furnace tubes. Such construction of the heating furnace has significant influence on its life time and prompt attaining rating power. In previous version of the KWM-SG heating furnace there was revision cleaning hole that facilitate access to convection ducts.
KWM-SG heating furnaces were equipped to thermal-resistant wide furnace door and fill-up door with purpose-made thermal gasket in the front of the heating furnace body. Whole body was covered with high-grade thermal insulation which is protected by steel casing. Central heating furnaces KWM-SG must be installed according to standard PN-91/B-02413 and BN-71/8864-27 concerning open vent water heating installations safety and open vent expansion tank.
Exploitation of KWM-SG heating furnaces is cyclical. It consists in one-shot fill-up with fine coal, firing it up from the top with use of small amount of paper and wood and starting up controller and blower. After having obtained previously set temperature the blower turns off and controller automatically turns into hold mode. The blower shall be started again when temperature falls under set value. When the fuel is burnt-out the controller turns off automatically. In order to launch the heating furnace once more it is necessary to remove ash from ash pan and furnace chamber and fill up fuel tank and fire up the heating furnace.
ST–81 temperature regulator is intended for charging CH boilers. It controls the water circulation pump, hot usable water pump and the fan. Four optional modes of the pumps operation: house heating, boiler priority, parallel pumps, summer mode. The controller is casing is adjusted to be assembled in the boiler is installation.
Wyrażam zgodę na przetwarzanie przez PPHU Kotłospaw danych osobowych podanych w formularzu. Pana/Pani dane będą przetwarzane w celach związanych z udzieleniem odpowiedzi, przedstawieniem oferty usług. Administratorem podanych przez Pana/ Panią danych osobowych jest PPHU Kotłospaw z siedzibą ul. Szenica 38, 63-300 Pleszew.
Call +48 600 494 315 or email us to get advise from our consultants.
Producent Kotłów C.O. PPHU KOTŁOSPAW
ul. Szenica 38, 63-300 Pleszew
+48 62 597 14 78 +48 62 597 14 79 firstname.lastname@example.org